SCH Number 2005091071
- Gateway Village Area Plan
- SWRCB, as the responsible agency, will be issuing a water supply permit. The Riverstone Root Creek Water District will construct 1 tank (provisions for future second tank) and 3 wells to supply water to an estimated 858 homes, roadway frontage and park landscape, and agricultural turnouts to a new Riverstone Development. Well number 1 will have 250 HP and produce 1,300 gallons per minute, well number 2 will have 400 HP and produce 1,600 gpm, and well number 4 will have 300 HP and produce 1,400 gpm. A small 6-foot by 9-foot by 8-foot structure will house the sodium hypochlorite pump and plastic drums at the 3 wells sites and an injection quill will chlorinate the water before the water enters the hydropneumatic tanks at each site. A compressor will be attached to the tanks and space will be left for the addition of future wellhead treatment at these sites, as needed. Well 1 and Well 2 will connect to the 18-inch distribution line through 10-inch piping and then will connect to the one 1,000,000 gallon tank 3 600-gpm pumps (provisions for future 4th 600-gpm pump) will be installed to pump the water through 16 inch piping to an installed 7,500 gallon hydroneumatic tank. !2-foot pole mounted LED lighting wil lbeinstalled across the site. A 6-foot chain link fence will surround the site with barbed wire above it. A flow meter and SCADA system will be installed. From the hydropneumatic tank the water will be pumped through 16-inch piping to the already installed water system piping mains consisting of 12-inch, 14-inch, and 18-inch piping. Well 4 will connect to the water infrastructure with 12-inch piping. The project will provide for the operation of these systems.
4 documents in project
|NOD||Madera County||Operation of Riverstone Village A Water System|
|FIN||Madera County||Gateway Village Area Plan|
|EIR||Madera County||Gateway Village Specific Plan|
|NOP||Madera County||Gateway Village Project|
Disclaimer: Summaries of the notices may take several days to appear on CEQAnet. Again, the publishing of information on CEQAnet does not factor into when such notices were received and posted by the SCH. Contact the SCH for copies of an NOE or NOD that has been posted at OPR.